Altrac LPG-Propane Fuel Sensor (SN110)
Hall Effect Sensor (Plugs into dial on tank)
6-Pin Deutsch Connector (plugs into Accessory Port on Altrac wiring harness)
Intrinsically Safe Barrier Device
|Max Length (with Extension)||500' (150m)|
|Min Propane Level||Inaccurate below 20%|
|Max Propane Level||Inaccurate above 80%|
|Sheath||Nylon sheath for rodent protection|
|Calibration||Pre-calibrated. No need to calibrate|
Extension Cables (SN110_EXT_X)
Altrac offers extension cables for the SN110. Each extension comes with two connectors in order to create an easy, waterproof connection. Contact email@example.com for more information.
12VDC. The wind machine battery must be connected for the fuel sensor to function properly.
500 ft (150m)
The propane fuel sensor is accurate to +-10% when the dial is reading between 20-80%. We cannot guarantee accuracy when dial is below 20% or above 80%.
Normally you will see percentage full of your tank:
If the probe is disconnected you will see:
If the probe is connected but giving a value outside of its range, you will see:
Cost of Extension Cable:
$.60/ft + $40 for connectors and labor. Cable is rated for direct burial. Connectors are removable if you want to pull the wire through conduit for added protection.
While the wind machine is running, the propane level will not update. This is a firmware issue that will be resolved in a future release. 1-5-2022. See below for an example.
Please sign in to leave a comment.